Emergency rescue plan for elevator I. Elevator emergency plan 1. Upon receipt of alarm from owners or passengers trapped in the elevator, they should be immediately informed of security fire control room, and at the same time, the time of receiving report and finding time shall be recorded. 2. Security fire control room after receiving the report should be on the one hand through the monitoring system or walkie-talkie to understand the location of the elevator trapped people, the number of people trapped, the situation and the elevator where the floor, on the other hand through the walkie-talkie to the security manager, contact the maintenance unit Go to rescue. 3. After receiving the report, the security manager immediately arrived at the scene or dispatched officers to contact the trapped passengers and comfort passengers. Passengers were asked to remain calm and patiently seek help. In particular, when a trapped passenger is scared or impatient and tries to escape by such extraordinary measures as breaking the door, he / she should patiently advise passengers not to panic and impatience. Do not blindly take unnecessary actions so as to prevent the danger from expanding. Note that in the process, the scene can not always leave the scene, we must continue to dialogue with trapped persons, keep abreast of the emotional and health status of trapped persons, and promptly report the situation to the general manager of the company or duty leader. 4. Maintenance unit manager or on duty personnel to receive the report, they should immediately sent to the scene to rescue, call the elevator maintenance company to repair the phone. 5. If neither the maintenance organization nor the elevator maintenance company is able to rescue or rescue within a short period of time, it should seek assistance from the public security department or the fire department as necessary (explain the reasons and circumstances of the request). Before asking for help from the public security and fire departments, you should obtain the consent of the general manager or the leader on duty. 6. During the rescue process, if any one of the trapped passengers is found to be fainting and unconscious (especially
Elderly or children), medical staff should be immediately informed the scene so that trapped personnel can be rescued after rescue.
7. After the trapped people are rescued, the security manager or on-duty foreman should immediately express their condolences to them and understand their physical condition and needs, and ask them to provide their names, addresses, telephone numbers and reasons for coming to this district. If the trapped person left illegally, it should be recorded and archived for the record. 8. trapped rescued, should immediately lift maintenance company to identify the cause of the malfunction, repair before resumption of normal operation. 9. The security manager or on-duty foreman should record in detail the circumstances of the incident, including the time of arrival, the arrival time of the security and maintenance personnel, the notification and arrival time of the elevator maintenance company, the rescue time of the trapped persons and the basic conditions of the trapped persons, Elevator resumes uptime. If there are public security, firefighters, medical staff present, should also record the entry and departure time, vehicle number; trapped persons were injured, should record the wounded and was taken to the hospital. 10. Maintenance unit manager or duty personnel should record in detail the time of failure, the reasons for the rescue and repair time. Emergency Outbreak Contingency Plan 1. Upon receipt of the black out notice, the management department shall notify each household and business beforehand of the blackout line, area, time, elevator usage and safety precautions, etc., and issue a blackout at the main entrances and exits Notice; the same time, the maintenance unit should be prepared to deal with the strain before the power outage 2. In the absence of any notice, a sudden power outage, the maintenance unit should immediately confirm whether the internal power failure or external blackouts. If the internal power failure, should immediately send people to find the reasons to take measures to prevent the failure to expand; if the external power outages, on the one hand to prevent sudden calls cause an accident on the one hand to call the power outage check the situation, to understand when the resumption of supply
Electricity, and inform the management of the operation of the Department.
3. The security department immediately sent with the maintenance unit separately went to each floor to check the elevator operation and found that the lift off immediately in accordance with the emergency plan for rescue of people trapped in the elevator. 4. arrange staff to the district of the main entrances and exits, elevator hall to maintain order, security and strengthen security measures to prevent someone from creating chaos, in troubled waters, if necessary, close the door. 6, preventive measures for unexpected power outages: 1) maintenance units should always check the emergency lighting and emergency broadcasting system to ensure normal. 2) The management department should remind office tenants and businesses of setting up some emergency lights or candles to prevent power failure. 3) Security Department, maintenance unit in addition to patrol, maintenance torch, it should also be equipped with portable emergency lighting, and always charge and maintain, remain intact. Third, emergency treatment in case of fire ⒈ timely contact with the fire department and report the leadership. ⒉ press the fire function elevator "fire button" so that the fire elevator into the fire operation, for firefighters use; for firefighting function elevator, the elevator should be immediately driven to the ground floor and cut off the power or stop the elevator The floor of the fire has not yet spread. Advise passengers in the car to keep calm After the implementation of the rescue program, organize and divert passengers to leave the car and withdraw along the safe passageway, placing the elevator in a state of "stop running", closing the hall door and car door by hand and cutting off the total power of the elevator . When there is a fire in a hoistway or a car, immediately stop the elevator to divert the passengers, cut off the power and extinguish the fire with a fire extinguisher. ⒋ For a fire in a lift with a shared hoistway, immediately leave the rest without fire
The elevator stops far away from the area where the fire has spread, or it can be given to firefighters for fire fighting.
⒌ In the event of a fire in an adjacent building, you should also stop the ladder to avoid any trouble caused by a power outage caused by a fire. Fourth, when an earthquake occurred. According to the emergency measures released by the local people's government to the residents in the forecast area, it is decided whether the elevator will stop and when it will stop. ⒈ For the earthquake magnitude and intensity, before the earthquake did not issue a temporary earthquake prediction and sudden earthquake, once the earthquake induction near the stop, the passengers left the car to avoid nearby, such as passengers trapped in the car is not allowed to escape, Stay calm and wait for help. ⒉ elevator after the earthquake should be checked and test run, the normal rear can be restored to use, when the magnitude of four below the intensity of 6 degrees below, the elevator check: whether the power supply system anomalies; hoistway, rail, car without exception ; To overhaul the speed to run up and down the entire process and found abnormal stop immediately, and make the elevator reverse run to the top of the station stop ladder, inspection and repair by professionals until the upper and lower work together without exception and after many round-trip trial operation, the parties Can be put into use. Fifth, when wet water occurs. In the face of typhoons, thunderstorms, floods and other inclement weather, preventive measures should be implemented to strengthen the elevator inspection inspection, shut down the engine room windows and doors. Elevator engine room roof or doors and windows leaking and water; pit due to poor construction of the waterproof layer and seepage water; heating and water pipes, fire hydrants, household water leakage caused by wet elevator accident, in addition to the use of construction facilities blocking Leakage measures, but also take emergency measures: When the pit found a small amount of water or water seepage, the elevator should be parked in more than two floors, terminate the operation, disconnect the total power supply. ⒈ when the floor flooded so that the shaft or pit into the water, the car should stop at the inlet layer
On the second floor, stop power down to prevent the car into the water.
⒉ pit wells or room when a lot of water, should immediately stop, disconnect the main power switch, to prevent short circuit, electric shock and other accidents. ⒊ Wet water should be quickly cut off the source of leakage, trying to make electrical equipment without water or less water. ⒋ wet water elevator should be dehumidified, such as to wipe, hot air dry, natural ventilation, replacement of pipelines and other methods. Confirm that the wet water is eliminated, the insulation resistance meets the requirements and can not be put into operation after the test ladders have no abnormalities. Computer-controlled elevator, but also need to carefully check to avoid burning the circuit board. ⒌ After the elevator resumes operation, fill in the wet-water inspection report in detail and record the cause and treatment of the wet water well and record the precautionary measures.
Previous: How does the elevator work